Point-to-Point Wireless Repeater Unit, Add up to 15 Repeaters to your Twin Link System
See It In Action
In this example, a wireless link is needed between a reservoir and a pump station. The Input Node will measure the incoming 4-20mA signal from the reservoir level sensor, and the Output Node will output 4-20mA to the pump controller, which will switch the pump on and off (thus controlling the water levels in the reservoir).
The reservoir is over a hill, so there is no line of sight between it and the pump station. By placing a Repeater at the top of the hill within line of sight of both the Input and Output nodes, a successful link can easily be made.
RF data rate: 250Kb/s
RF frequency range: 2405-2475MHz
RF transmission power: +20dBm (Optional low power setting [10dBm] selectable in software)
Transmission range: Up to 0.9mi (1.5km) LOS with supplied antenna (WG-3DBI). All nodes must be set to full power (+20dBm) for max range. Transmission distance may be limited by regional power restrictions.
RF receiver sensitivity: -110dBm
Number of RF channels: 15
Number of wireless nodes: Up to 17 nodes per mesh (Twin Link plus up to 15 Repeaters)
Spreading method: Direct sequence
Power supply: 9–36V DC, 2.5VA max
Casing: 35mm DIN rail mount casing. Installation Category II; Pollution Degree 2; Flame resistant
Ingress protection rating: IP20 – install in a protective enclosure
Dimensions (H x W x D): Unit body: 3.98 x 0.91 x 4.72″ (101 x 23 x 120mm), With included antenna: 5.91 x 0.91 x 5.75″ (150 x 23 x 146mm)
Weight: 4oz (113g), with included antenna and plugs
Operating temperature: -4 to 131°F (-20 to 55°C)
Storage temperature: -4 to 149°F (-20 to 65°C)
Operating humidity: 0–85% non-condensing
Altitude: 2187yd (2000m)
Certifications & Compliances
FCC ID: 2ACTT-1409: 47 Code of Federal Regulations; Part 15 – Radio Frequency Devices; Subpart C – Intentional Radiators, including Section 15.247 – Operation in the band 2400 –2483.5MHz
SAS/ANS 4268:2012: Radio equipment and systems – Short range devices – Limits and methods of measurement
ETSI EN 300 440-2, V 1.4.1, 2010: Electromagnetic compatibility and Radio spectrum matters (ERM); Short Range Devices (SRD); Radio equipment to be used in the 1GHz to 40GHz frequency range; Part 2: Harmonised EN under article 3.23 of the R&TTE Directive
EN 301 489-3 V1.6.1, 2013: Electromagnetic compatibility and Radio spectrum Matters (ERM); Electromagnetic Compatibility (EMC) standard for radio equipment and services; Part 3: Specific conditions for Short Range Devices (SRD) operating on frequencies between 9kHz and 40GHz
Smart, simple software to program your non-Zen series products
Use Define ToolBox software to program your non-Zen series product via your PC. It configures:
- Merlin Universal Digital Indicator
- Twin Link Point-to-Point Wireless Transmitter Receiver
- All Define Instruments Transmitters (Javelin, TM-2DLI, TM-2HL, TM-2HLI, TM-4DPI)
ToolBox offers a simple interface for connecting to your compatible device, and a range of flexible configuration options, including an extensive library of pre-calibrated ranges and linearization tables for advanced scaling.
|P2P-R||Point-to-Point wireless repeater unit|
|P2P-TWIN-LINK||Point-to-Point paired I/O units (P2P-I + P2P-O)|
|Bridge Key||USB Bridge Key and communications kit (required for software configuration)||Not FCC approved.
|Antenna Upgrades||Click here for antenna upgrade options|
|Define ToolBox||Simple utility for setting up your Point-to-Point system||Free download|